Manoah House – Fire Pump Replacement
Awarded Maintenance Contract in July 2014.
Post completion of first monthly inspection it was identified the the diesel pump power was fluctuating significantly. Our in-house diesel mechanic diagnosed that the governor and fuel pump had failed and required replacement. With a further investigation we identified that the pump was running to end of life and offered the client the option to replace the pumps.
As the Aged Care was occupied and operating we needed to have a custom pumpset built like for like to ensure the downtime operation was minimal.
With our wide range of suppliers we managed to source a “like for like” replacement from the eastern states which also could be supplied at short notice ensuring our client was satisfied and all occupants were safe.